AVG TEMPERATURE CONTROL VALVE 20mm with insulation
- 1.20 KGS
- Free Shipping
AVG TEMPERATURE CONTROL VALVE - TCV20-i 20mm with insulation
TCV - Temperature Control Value Standard (red cap) Suitable for applications requiring blended water.
plumbonline have have the complete range from AVG (Australian Valve Group) listed online for your seamless selection the full specification is presented for you in clear and easy to read format, if you need assistance get in touch!
The TCV-i (Red Cap) is designed for applications requiring blended water. The TCV-i Prevents superheated water being delivered when installed on water heater systems.
- Mixes hot water and cold water to deliver blended water
- Ideal for commercial applications requiring blended water
- Controls maximum temperature of delivered water
- Prevents superheated water being delivered when installed on water heater systems
- Accurate control of outlet temperature
- Incorporated strainers and check valves Protects valve and check valves from impurities in the water supply
- Tamper-proof adjustment
- Meets Australian Standard for potable water supply
- Individually tested and calibrated Every valve is tested to ensure higher quality and performance
- Factory set at 65°C
NOTE! - The TCV is factory set at 65°C. If required to be used as a safety valve the TCV must be commissioned on site to no more than 50°C by licensed plumber as per AS3500.
Valve Specifications (20mm & 15mm TCV)
- Cold water supply temperature: 5°C - 25°C
- Hot Water supply temperature: 65°C - 99°C
- Safe adjustable outlet temperature range: 40°C - 50°C
- Factory set temperature: 65°C maximum (Must be commissioned onsite by installer)
- Accuracy of outlet temperature: ±3°C - tested to AS4032.2
- Minimum temperature differential (between hot supply and outlet temperature): 15°C
- Supply pressure, static : 1600kPa maximum
- Supply pressure, dynamic : 500kPa maximum
- Pressure supply imbalance, dynamic : 2:1 maximum (at time of commissioning )
- Maximum permitted pressure variation in either supply in order to control outlet temperature to ±3°C: ±10 % maximum (from supply pressure at commissioning )
- Flow rate minimum: 4 litres/min
To ensure safety, the TVA must be installed and maintained strictly according to AVG’s installation instructions, Australian Standards and local regulatory requirements. AS3500 now calls on all valves & pipe work to be insulated. AVG provide the insulation & cable ties with the tempering valves
The tempering valve must be installed by a licensed plumber and in accordance with AS/NZS 3500, relevant local requirements and the following:
- Tempering valve must be fitted in accordance with the instructions supplied with the valve
- It is recommended that isolating valves are fitted immediately upstream of both hot & cold inlets to the tempering valve This allows convenient access to isolate the tempering valve in the event that the strainers need to be cleaned
- It is recommended that the tempering valve be installed as close as possible to the point of use, however it may be fitted anywhere on the hot water supply line.
- If the the tempering valve is fitted at the point-of-use, there must be a minimum one (1) metre pipe run between the valve mixed water outlet connection and the tap
System Supply Pressures
- Tempering valves provide optimum performance when installed with hot and cold water supplies of equal dynamic pressure, ie with the water flowing. (The static supply pressures often give no indication of the dynamic supply pressures). It is recommended that the hot and cold water supplies to each tempering valve be controlled via their own pressure control valve. In most domestic installations it should be possible to fit one control valve at the property boundary to control pressure to the whole site. For commercial installations it is recommended to fit a pressure control valve on each inlet to the tempering valve.
- Prior to adjusting the tempering valve it is necessary for the hot water heater to be switched on and delivering hot water at the recommended temperature. If the water heater has an adjustable thermostat it is recommended that the thermostat be set to 65ºC. Ensure that the water heater has reached the set temperature before commissioning the tempering valve.
- Test the mixed water temperature at the nearest outlet being supplied by the tempering valve. The tap should be opened to allow a flow rate of at least four (4) litres/minute.
- A thermometer must be used to ensure the correct mixed water temperature is achieved.
- Allow the water to run for at least one minute to ensure the mixed water temperature has settled after each adjustment.
- To adjust the mixed outlet temperature of the tempering valve the cap should be removed to gain access to the adjusting spindle. Using the special tool moulded into the top of the cap rotate the adjusting spindle to achieve the required temperature. The spindle should be rotated - clock wise to reduce the temperature, anti-clock wise to increase the temperature - until the desired temperature is reached. See adjustment diagram provided with the valve.
- Once the required temperature is achieved the cap should be snapped onto the valve to prevent accidental adjustment.
- When the tempering valve has been commissioned, the commissioning label must be completed by the installer and affixed to the water heater in a prominent position, (or other suitable position or as specified by the Local Authority).
Just installed, but should work well to bump down the super-heated water from my solar HWS and save plastic mixers, pipework, etc, from damage, whilst being able to keep the temp up to send the hot water a long way to a bathroom at the back of the house. Fast delivery, thanks.